600V or less
Sino-cables XHHW-2 type aluminum conductors are annealed AA-8000 series Aluminum Alloy, compact stranded. Insulation is an abrasion, moisture and high-heat resistant black cross-linked polyethylene. Conductor sizes AWG 2 and larger listed and marked sunlight resistant in black only.
Copper conductor is also available.
XHHW-2 conductors meet or exceed UL Standard 44 .Federal Specification A-A-59544, and requirements of the NEC Type XHHW-2 meets and exceeds all construction requirements of ICEA S-95-658(NEMA WC 70)-Non shielded 0-2kv Cables, with testing frequencies based on UL requirements.
2.High-Heat and Moisture and Sunlight Resistant.
3.VW-1 or higher required by UL.
1.XHHW-2 conductors are primarily used in conduit or recognized raceways for services, feeders, and branch circuit wiring as specified in the National Electric Code(NEC).
2.May also be used in wet or dry locations at temperatures not to exceed 90℃.
3.Voltage rating for RW90 cable is 600V.
steel ＆ wooden reel, wooden reel, steel reel, in coils on wooden tray, or other requirements by customers.
|W E I G H T S. M E A S U R E M E N T S|
(AWG or kcmil）
|* Ampacities for not more than three conductors in raceway, based on ambient temperature of 30°C per Table 310-16 of the 2005 National Electrical Code (NFPA 70-1990). |
60 °C - When terminated to equipment for circuits rated 100 amperes or less or marked for 14 through 1 AWG conductors.
75 °C - When terminated to equipment for circuits rated over 100 amperes or marked for conductors larger than 1 AWG.
90°C - XHHW wet or dry locations for ampacity adjustment purposes using NEC section 310.1.
* All values are nominal and subject to correction.